HVAC Services in Hudson, WI
If you're looking for reliable HVAC repair in Hudson, WI, and the surrounding area, look no further than Stellar Techs. We're a home services company that serves Hudson, western Wisconsin, and eastern Minnesota.
At Stellar Techs, we pride ourselves on providing high-quality services to our clients. We have decades of experience and are available 24/7 to handle any emergency service needs you may have. Our clients are our top priority, and we strive to provide exceptional customer service every time.
If you're considering any of our services, don't just take our word for it - check out our hundreds of 5-star reviews from satisfied clients. We're confident that you'll be impressed with our work and dedication to our clients.
We're proud to serve Hudson and we look forward to helping you with any of your home service needs. Contact us today at 715-564-4328 to schedule a consultation or service appointment.
Our air conditioning repair and installation service is world-class, and our technicians are trained to provide prompt and polite service. We take pride in our commitment to quality and getting the job done right the first time. Whether it's a routine maintenance check or a complex repair, our team has the knowledge and resources to keep your air conditioning system running smoothly and efficiently.
If your furnace or boiler is making noises, has an odor, leaks, or any other issue that needs repair, our technicians have the experience to provide the necessary repairs. We’ve worked with all the leading furnace & boiler makes and models. No matter if your unit is an older model or a newer brand, with over 40 years of servicing heating systems, our technicians will be able to diagnose any repairs and provide the service you need to keep your heating working properly.
Stellar Techs can help you find the perfect indoor air solutions to remove pollutants such as dust, pollen, and mold spores from your home or office. These systems can improve indoor air quality, reduce allergies, and help prevent respiratory problems. We offer filter-based purifiers and UV light purifiers, which kill microorganisms rather than trapping them in a filter.
Plumbing Services in Hudson, WI
At Stellar Techs, we're proud to offer select plumbing services in addition to our HVAC repair in Hudson WI.
Got hard water? Noticing any odor or unpleasant taste in your drinking water? Our water treatment systems are designed to purify your home's water and make it softer. We use a multi-stage filtration process that removes contaminants such as chlorine, bacteria, and sediment, leaving you with clean and refreshing water.
Are you tired of taking cold showers or having to wait for ages for the water to heat up? We offer top-notch water heater repair and installation services for both homes and offices. Say goodbye to the frustration of dealing with malfunctioning water heaters - our skilled technicians are trained to efficiently take care of your needs. We service and replace all gas and electric, traditional, and tankless hot water heaters.We are not only experts in their field but also polite and prompt, making sure that your time and comfort are always prioritized. With our commitment to getting the job done right on the first visit, you can be assured that your water heater will be up and running in no time. We thrive on keeping our clients satisfied with our work, which is why we guarantee all our services.
Are you experiencing plumbing problems? Don't despair! Our team of skilled technicians is just a phone call away. We specialize in repairing plumbing fixtures, and we do it at an affordable price. Our clients love us because we hire only the most polite and professional technicians in the industry. Whether your pipes are leaking, your toilet is clogged, or your sink is backed up, we have the tools, experience, and qualifications to get the job done right. Don't risk making the problem worse by attempting to fix it yourself. Call us and let us take care of your plumbing issues with speedy and reliable service.
Recent Jobs and Reviews in Hudson, WI
Our Local Reviews by City
Job Locations and Reviews
09/26/23 LOGAN STELLAR PERFORMANCE MEMBERSHIP HEATING SEASON INSPECTION. Performed gas leak test—pass. Checked thermostats—pass. Checked furnace air filter & blower compartment—pass. Tested the water for hardness and total dissolved solids—pass The furnace, and water softener are operating properly at the completion of the inspection. Thank you for choosing Stellar Techs Home Services! We appreciate the opportunity to serve you!
09/22/23 JOSEPH & LOGAN STELLAR PERFORMANCE MEMBERSHIP COOLING SEASON INSPECTION. Checked thermostats—pass. Checked all AC components, electrical components, refrigerant levels, coils, drain, line insulation, temperatures and pressures.— The air conditioner is operating properly at the completion of the inspection. Thank you for choosing Stellar Techs Home Services! We appreciate the opportunity to serve you!
09/01/23 JOSEPH REPLACE DAMPER. The supplier sent the wrong damper. I have re-ordered the damper with explicit instructions so they get it right. We will reschedule once we have the correct damper. We will open the box before coming out to make sure it is correct. We will give you a call to schedule when we have the correct damper. 09/20/23 JOSEPH I returned it and took out the old damper. Installed the new damper. Checked system operation. Everything is operating properly. Sealed all of the joints on all dampers as they were extremely leaky. Discussed the leakage and the effects that it has on the system with Joe and Linda. Everything is operating properly at the completion of the call. Received final payment info on the personal check. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
LOGAN AND LANCE, 9/14/23, WHOLE HOME INSPECTION Gas leak check—pass Checked thermostats—pass. Checked furnace air filter & blower compartment—pass. Checked water heater tank and operation—pass. Checked all AC components, electrical components, refrigerant levels, coils, drain, line insulation, temperatures and pressures.— Tested the water for hardness and total dissolved solids—passed Customer authorized … The furnace, air conditioner, water heater and water softener are operating properly at the completion of the inspection. Thank you for choosing Stellar Techs Home Services! We appreciate the opportunity to serve you!
Stellar Performance Membership Cooling Season Inspection. Preventative AC maintenance checklist: Performed gas leak test—pass. Checked thermostat—pass. Checked furnace air filter & blower compartment—pass. Checked water heater operation—pass. Checked all AC components, electrical components, refrigerant levels, coils, drain, line insulation, temperatures and pressures—pass. Line set insulation is aging and may need replacement soon. Also checked the garage mini-split and garage heater—pass. ECOBEE Lite thermostat installation. Helped the customer set up Wi-Fi and the smartphone app. The mini-split, garage heater, furnace, air conditioner and water heater were operating properly at the completion of the inspection.
We appreciate your honesty and your feedback.
AC wire to condenser repair. Checked the circuit board, fuse on board and low voltage. All passed inspection. Repair of the AC wire.
08/31: Whole-house water softener installation. Shut off the water to the house, drain the system and cut out the old water softener connections. Installation of new water softener and connection. Performed a start-up on the water softener and it is operating properly. 09/12: Returned to install the feet on the brine tank grid. Once the feet were installed, added salt to the grid and brine tank. Put the system through regeneration to make sure that the water is soft.
New customer enrollment in Veterans HVAC Membership plan.
09/07/23 JOSEPH & LANCE CHECK HAIL,DAMAGE ON AIR CONDITIONER The unit is damaged from a recent hail storm. The fins and tubing are old and brittle. Attempts at straightening will result in worse damage and refrigerant leaks. It is likely that this will occur even without attempting to fix the fins. We highly recommend replacing the outdoor and indoor coils in lieu of making the very bad choice of trying to straighten the fins.
09/07/23 JOSEPH & LANCE AC AND FURNACE ARE NOT TURNING ON Found blower door switch stuck. Popped it loose and then the furnace blower and AC started operating. Checked all wiring and switches on the furnace board. Found added jumper wire that was preventing two-stage heat operation. Removed the jumper wire. Put all switches in the correct positions. The AC fan speed was still in the factory setting (high speed). The installing company failed to set this properly. Set the switches so the airflow is correct for the capacity of the air conditioner. We will be back next week to perform a complete system checkout. Due to the wrong airflow setting, the refrigerant levels set by the installing contractor are going to be incorrect. Provided several thermostat replacement options. We will bring the various thermostats with us when we return next week for the inspection. Received payment in full for today’s work. The furnace and air conditioner are operating at the completion of the visit. Th
09/06/23 JOSEPH & LANCE AC IS NOT COOLING Checked the furnace filter, blower motor, and blower wheel. They are operating properly. The thermostat is operating properly. Went to the outdoor unit and the compressor was not running. The outdoor coil was also extremely dirty. The insulation on the piping was eaten away by rodents. Provided options to the homeowner. They chose to have us clean the outdoor coil, replace the high-voltage storage device and replace the insulation. After performing the repairs and cleaning the unit, the air conditioning is operating properly at the completion of the call. Received payment in full by cash. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
09/06/23 JOSEPH & LANCE CONVERT FIREPLACE FROM LP TO NG Attempted to make the conversion, but the parts are not the correct parts. Evan called the manufacture to order the correct parts. They are not available. The unit is too old. We discounted the work by half since we did disassemble everything, but could not put it back together with the wrong parts. Evan is going to purchase a different fireplace insert and have a fireplace company install it. Received payment in full for today’s work on visa card. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
Provided updated quotes for system.
09/05/23 JOSEPH & LANCE AC IS NOT COOLING Found bad high voltage storage device. Offered membership. Replaced high voltage storage device. Ran unit to test and check refrigerant levels. Refrigerant was low which indicated a leak. Got approval to add sealant and refrigerant. The air conditioner is operating properly at the completion of the call. Received final payment in full on VISA Card. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
09/05/23 JOSEPH & LANCE AC MOT KEEPING UP Discussed the membership plan. They signed up for the membership. Found very dirty filter at furnace. Ordered case of filters for home delivery. No water panel or bypass damper in humidifier. Looks like it doesn’t operate properly. Checked condenser. Outdoor coil is very dirty. High voltage storage device is good. Cleaned the coil with the owners hose. Received final payment in full on VISA Card. The air conditioner is operating properly at the completion of the call. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
08/14/23 JOSEPH & LANCE CHECK SITE FOR RUNNING THE HOOD DUCTWORK. There was no rough-in dimensions available. We will return after the cabinet contractor marks the rough-in layout on the wall. 08/24/23. JOSEPH & LANCE Installed pipe through the wall. Replaced the receptacle and added a cover plate. 08/31/23 JOSEPH & LANCE COMPLETE THE EXHAUST BLOWER VENT AND ELECTRICAL INSTALLATION. Added extension on interior piping. Connected all piping from the blower to the outside wall. Installed the exhaust hood. Installed the blower into the hood. Tested the blower and light operation. The blower and light are operating properly at the completion of the installation. Received payment in full on check 1411. We did not charge for the actual installation of the blower. Ashlei has waited long enough to have this done. We are including it as a favor to Ashlei! Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
REPLACE VENT RAIN CAPS ON GARAGE HEATER AND MAIN CHIMNEY VENTS. DAMAGED BY HAIL STORM.
From Wisconsin code: (L) Showers. 1. Prefabricated plastic showers and shower compartments shall conform to ANSI A124.1.2. 2. Except for combination bathtub-shower units, waste outlets serving showers shall be at least 2 inches in diameter and shall have removable strainers of sufficient strength for the anticipated loads.
08/08/23 JOSEPH Sold complete system replacement. 08/17/23 - 08/18/23 JOSEPH & LANCE Installed a LENNOX variable capacity system with a 99% furnace, LENNOX 23 SEER air conditioner, LENNOX Pureaire air purification system and LENNOX iComfort control system including the LENNOX Zoning System. LENNOX will rebate back $900. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
08/14/23 JOSEPH & LANCE INSPECT MINI-SPLIT HEAT PUMP DAMAGE AFTER JULY 24, 2023 STORM The fins on the west side of the coil are damaged. They need to be straightened by combing and by individually lifting the severely flatted blades one at a time until able to be combed. Requires complete removal of the cabinet surrounding the coil in order to properly perform the repair. The cabinet will be reinstalled after the repair. This is a new unit which was installed on 07/21/23.
08/11/23 JOSEPH & LANCE INSTALL PROPER WIRING CONNECTION FOR THE DEHUMIDIFIER Ran a new circuit for the dehumidifier including circuit breaker, wire, duplex remodeler box, duplex receptacle and receptacle cover. Tested circuit and dehumidifier operation. They are operating properly at the completion of the job. Received final payment in full on VISA. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
08/08/23 JOSEPH & LANCE REPLACE DOOR SWITCH ON FURNACE AND CHECK WHY HUMIDIFIER IS TRIPPING THE BREAKER We replaced the door switch and rewire the furnace so that the door switch was not bypassed. Checked the operation and it is working properly. Also discovered that the humidifier water panel was literally falling apart. It was not the humidifier that was tripping the breaker, but a central dehumidifier. Provided options on replacing the water panel of the humidifier and correcting an electrical issues with the dehumidifier. The homeowners authorized replacing the water panel and correcting the electrical issues. We will be ordering parts for the electrical portion. Replaced the water panel while we were there. Received a down payment for the future work and payment in full for all work completed today. The down payment will be applied to the job that we will schedule once we receive the parts. The balance of the electrical work will be paid upon completion. Thank you for choosing S
08/07/23 JOSEPH & LANCE RETURN TO CLEAN BLOWER AND ADD REFRIGERANT Pulled and clean the furnace blower assembly. Added refrigerant and sealant to the system and balanced it to manufacturer specifications. Also re-insulated the suction line outdoors with new UV resistant insulation. The air conditioner is operating properly at the completion of the call. Received payment in full on Visa card. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
Amy, thank you so much for letting us know how awesome Chris did getting your AC repair scheduled! We hope the service was as great at the call!
08/04/23 JOSEPH AC IS NOT COOLING Found that the indoor blower was working. Outdoor fan is running but could hear compressor trying to start, but not starting. Opened controls compartment and found mouse nest and burned off starting wire between the high voltage switch and the compressor booster. Replaced the wire. Also replaced other terminal ends on two other wires. Restored power to the unit. The air conditioning is now operating properly. Received payment in full on VISA. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
08/04/23 JOSEPH FAN BLADES ARE BROKEN OFF ON OUTDOOR UNIT Removed old broken blades and installed new blades. Balanced the blades. Run tested the unit. The air conditioner is operating properly at the completion of the call. Received final payment in full on VISA. Thank you for choosing Stellar Techs! We appreciate the opportunity to serve you!
We appreciate you kinds words! Thanks for sharing!
We’re so happy you loved your experience and can’t wait to have you back for your next service appointment.
Thank you for taking the time to leave such a positive review! We're glad to hear you had a great experience with us.